A South-East Queensland nursery has implemented a 19.89kW Solar System to offset grid power following their QFF Energy Savers audit.
The farm has implemented a lighting upgrade, Power Factor Correction (PFC) and a 30.4kW Solar PV system to achieve annual energy savings over $14,700. The lights and PFC offer a payback period of under 3 years, with the PV payback around 5½ years. The Pump VSD and pressure transducer once implemented will allow the pump to operate at its Best Efficiency Point.
An energy audit for the on-site electricity usage recommended the installation of variable speed controls on pumps, replacement pumps with more energy efficient drive units, hot water system replacement, lighting replacement, air conditioning upgrade options & installation of solar photovoltaic system.
The audit identified several energy efficiency opportunities including regular checks for leaks in the irrigation and compressed air systems and a lighting upgrade. The audit recommended a 10kW Solar PV system to complement energy efficiency practices already in place, to further cut power required from the grid by 35% to save over $4,000 per year with a payback of less than 5 years.
The irrigation energy audit recommended adding variable speed drives to two dam pumps as they have varying duties in supplying centre pivot irrigators. The audit also recommended upgrading 100mm steel main pipe for transfer pumping to 125mm plastic. These initiatives would result in energy savings of over $41,000 per year and a payback period of around 1.5 years.
The irrigation energy audit assessed a number of irrigation systems, and recommended the addition of variable speed drives to an existing pumping station consisting of 2 x 7kW and 1 x 5.5kW fixed pumps. The upgrade would result in energy savings of 15% with a payback of 11 years.
A number of initiatives were recommended including replacing 400W mercury vapour high bay lights with 150W equivalents, adding insulation to hot water piping and the addition of a 30kW solar PV system. In total the measures will save nearly $11,000 per year with a payback period of 5.5 years.