The farm, near Stanthorpe, produces zucchini and eggplant and is irrigated for 9 months of the year depending on rainfall. Water is supplied from an on-site irrigation dam and is replenished from rainfall and bores. There is also a pump in the nearby Severn River.
It is a small site consuming approximately 31,000kWh per year at a cost of $8,500. The farm produces approximately 190 tonnes of eggplants and zucchinis.
The infrastructure contributing to the energy consumption onsite consists of:
- 5.5kW dam pump
- A packing shed with cold room
- 11kW river pump
- A small bore pump of unknown size
A recent energy audit showed how improving the current systems can lead to energy and cost savings. The energy audit recommended the following changes to improve efficiency and reduce costs:
- Installation of Variable Speed Drives on the pumps to better manage the different sizes and elevated blocks on the site and reduce the electricity consumption.
- Installation of a 20kW solar PV system on the packing shed.
- Lighting upgrade to LED on the packing shed, being able to reduce the electricity consumption for lighting by up to 50% and have a better light , so fewer fittings are required.
Table 1. Energy and cost savings from audit recommendations.
||Annual Energy Savings (kWh)
||Annual Cost Savings ($)
||Emission Savings (tCO2-e)
||Capital Cost ($)
||Payback Period (years)
|5.5kW VSD on dam pump
|11kW VSD on river pump
The grower has proceeded with all the recommendations, which have been measured in a Measurement and Verification (M&V) process, as outlined in Table 2.
Table 2. Estimated and Actual energy and cost savings.
|Energy Savings including exports (kWh)
|Cost Savings including exports revenue ($)
The lower cost savings compared to the estimated have been influenced by the low use of solar generation onsite. Only 9,400 kWh are being used onsite valued at $2,186 and 19,290 kWh are being exported to the grid with a revenue of $1,516. Also, 19,600 kWh are being imported from the grid at a cost of $4,560. If the farm was able to adjust energy usage to offset all the grid energy consumption, it would lead to higher cost savings as the revenue from feeding into the grid is lower than the cost of using energy from the grid.
From the implementation of recommendations in the audit, the farm has reduced energy consumption by 99% and costs by 48%, including feed-in revenue, with Carbon emission savings of 23.2 tCO2-e per year.
Table 3. Pre and post implementation energy, costs, and energy productivity improvements.
|Energy Consumption (kWh)
|Energy Productivity (kWh/tonne)
An energy audit is a good investment
An energy audit is a great first step in moving a business towards a more efficient future by reducing energy use, costs and carbon emissions onsite.
An energy auditor will review your past energy bills, your equipment and the way your business operates. They’ll show you where you’re using excess energy and explain what you can do about it. Find out about what’s involved in an energy audit HERE.
See our range of agricultural energy efficiency case studies HERE and Subscribe to our bi-monthly energy e-news HERE
If you have any energy efficiency related questions for the team get in touch at email@example.com.
The Energy Savers Plus Extension Program is delivered by the Queensland Farmers Federation with support and funding from the Queensland Department of Energy and Public Works.