The 4.3 ha farm with current production covering 0.5ha utilises automated propagation and irrigation systems operating 24 hours per day year-round producing around 300,000 units per ha per year. Energy consumption varies with the seasons, with the highest peak demand in winter due to heating operating overnight. As the nursery is planning to expand, production and electricity requirements are expected to increase by 15% per year over the next three years.
The annual energy consumption for the site during the 2018-2019 period was 26,953kWh at a cost of $6,500, and energy consumption on the farm consists of:
- Irrigation: including a booster pump and a bore pump.
- Propagation system: includes a hydronic heating system with a timer installed.
- Other minor uses: an office and staff facilities.
A recent energy audit showed how improving the current systems can lead to energy and cost savings, even with the projected increase in production. The audit recommendations are:
- Irrigation Pump Upgrade: replace the booster pump with a twice-size multistage Variable Frequency Drive (VFD) controlled unit and replace the mainline with a 90mm pipe, to increase the flow rate and meet the future irrigation requirements as the nursery expands.
- Bore Pump Upgrade: replace the bore pump with a double-flow rate unit to reduce the runtime to half (6 hours), allowing it to operate during the peak solar generation period in the future, reducing electricity demand from the grid.
- Hydronic Heating System Insulation: insulate the pipes and install a 250L hot water storage tank to increase the storage of an existing system.
- Replace Air Conditioner: replace the old office AC with a reverse cycle split system, improving its efficiency.
- A 30kW Grid Connected Solar PV: to match solar generation with the projected increase in energy consumption, including heating the water for the initial period, thereby reducing the overnight electricity demand given the use of the hydronic heating system.
Table 1. Costs and savings from audit recommendations.
||Annual Energy Savings (kWh)
||Annual Costs Savings ($)
|Capital Cost ($)
||Payback Period (Years)
|Irrigation pump and system upgrade
|Bore pump upgrade
|Heating system upgrade
|Air conditioner (AC) replacement
|30 kW Solar PV
The nursery has started implementing all the recommendations and at the time of writing, had upgraded the air conditioner and installed the Solar PV system. The savings made have been measured in a Measurement and Verification (M&V) process, as outlined in Table 2.
Table 2. Estimated and Actual annual energy and costs savings.
Energy Savings (kWh)
Cost Savings ($)
The solar system is being implemented in 2 stages, with a 15kW array and 27.6kW inverter already installed and another 15kW array to be added to the system in the coming years. The lower solar generation (less than 50% of the expected) has been mainly caused by incorrect inverter settings, which were fixed during the M&V process.
The mainline irrigation upgrade will occur in mid-2021 which will reduce the irrigation run time and allow it to be matched with the solar generation curve for better utilisation. On the other hand, the new bore pump still requires the spray nozzle upgrading used in the tank to aerate the water, allowing reduced operating hours to match pump use with the solar generation period.
The new larger bore pump without the required spray nozzle upgrade has increased energy use by 900 kWh per year and the heating system has increased its annual energy consumption by 1,800 kWh given lower temperatures during night-time. The energy consumption on farm during the 2020 period was 15% higher than in 2019, in line with the projected increases. The M&V determined that 5% is due to the expansion of the farm, 7% is driven by climatic factors and 3% is because of the incomplete upgrades of the irrigation system. Since the audit, the owner has also reconditioned the abandoned greenhouse which will be operative in 2022, increasing the irrigation requirements and energy consumption.
From the partial implementation of recommendations in the audit, the business has reduced energy consumption by 47% and costs by 52%, with Carbon emission savings of 11.9 t/CO2-e per year. With the remainder of upgrades and inverter settings corrected, savings are expected to improve to 96% by 2021.
Table 3. Pre and post implementation energy consumption, costs, and energy productivity improvements.
|Energy Consumption (kWh)
|Energy Productivity (kWh/ha)
An energy audit is a good investment
An energy audit is a great first step in moving a business towards a more efficient future by reducing energy use, costs and carbon emissions onsite.
An energy auditor will review your past energy bills, your equipment and the way your business operates. They’ll show you where you’re using excess energy and explain what you can do about it. Find out about what’s involved in an energy audit HERE.
See our range of agricultural energy efficiency case studies HERE and Subscribe to our bi-monthly energy e-news HERE
If you have any energy efficiency related questions for the team get in touch at email@example.com.
The Energy Savers Plus Extension Program is delivered by the Queensland Farmers Federation with support and funding from the Queensland Department of Energy and Public Works.